How to Check and Adjust Your Pressure Tank
If you have your own water booster pump system you probably have a pressure tank. It is important to check it every so often to ensure that it is functioning properly.
Note: It is important to turn off all power to the system and drain the system of any water pressure prior to checking your tank. You will depressurize your system by turning off the breaker to the pump and opening a faucet in your home. Leave the breaker off until you complete your check of the tank. Adjustments to a new tank should be done prior to installation.
You will need a gauge, preferably dial or digital, to check the pressure in the tank. A standard tire gauge with a Schrader valve will also work.
Follow the steps below to check and adjust pressure:
Tip 1: If you do not know the pressure switch setting of your system, look for a pressure gauge installed near the tank or pressure switch. Open a faucet and take note of your pressure gauge reading when your pump turns on, this is your cut-in pressure.
Tip 2: If you suspect that you have a ruptured bladder in the tank, tap on the top and the bottom when the system is pressurized. If the bladder is okay, the tank will make a hollow sound at the top and a dull thud sound at the bottom. You are verifying that there is compressed air at the top and water at the bottom.
Check out Pressure Vessel Suppliers in UAE, if you are looking to simplify your system and cut down on the time that it takes to check your pressure tank.